After a quick inspection our engineer found an incorrectly installed manhole that was retaining water. The drain also had a number of large gaps between the joints causing tissue to get caught and block the line.
We resolved these issues by removing the manhole and reseating it correctly. We then repaired the joints and then concreted the unused slippers within the chamber. This gave the drain a complete overhaul and was left in fully functional order.
- Client Whitehall Road
- Date April 4, 2014
- Tags Drainage Maintenance